voltage and current harmonics up to the 256th harmonic component in all phases;
THD I% distortion of the current curve;
THD U% distortion of the voltage curve, etc.
These studies are necessary for further installation:
condenser installations for reactive power compensation at the enterprise:
determination of the required power CU (kVAr) for each power transformer;
selection of protective chokes for compensating capacitors;
filters of power harmonics. To exclude the influence of harmonics generated by nonlinear consumers (UPS, frequency drives, contact welding installations).
Complete your application online.
We will contact you shortly and answer all your questions.